Verticle turbine pumps
We were instructed by Powerplant in Ritthem to overhaul the cooling-water pump for maintenance twice. During the inspection we found that one of the vortex breakers in the suction cup was broken and the other two showed tears. These were expertly repaired by our team. Bushings in the spider gear were replaced and installed using dry ice. The impeller was balanced, bearings were replaced and the exterior was provided with a new coating.