We have overhauled four cooling water pumps on behalf of a power plant in Ritthem. During the inspection it was found that one of the vortex breakers in the suction cup was broken and that the other two were torn. These have been professionally repaired by us. Running bushes in the spider have been replaced and mounted using dry ice. The impeller is balanced, bearings have been replaced and the outside has a new coating.